Thermally protected, specification grade compact fluorescent housing. For new construction non-insulated ceilings or where insulation can be kept 3" from housing.
Accommodates (2) 13W PL Double Twin Tube Compact fluorescent lamp. Furnished with preinstalled adjustable bar hangers.
Junction box is provided with four ½" KOs, one ¾" KO and four Romex knockouts with strain relief.
High temperature painted 22 gauge cold rolled steel.construction for maximum heat dissipation and rust protection. Adjusts vertically in plaster frame to accommodated ½" to 1-3/8" ceiling.
Two vertically mounted plug-in socket. Unitized optics guarantees proper trim to housing installation. Tool-less installation adjusts from inside the housing.
Thermally protected, current controlled ballast, will produce full light output, increase lamp life with no noise and flicker. Ballast supplied is manufactured by Advance.
Preinstalled bar hangers allow housing to be positioned and locked at any point within a 24" joist span and can be shortened for 12" joists.
They contain a double-headed real nail for secure attachment into the joist. Bar hanger nails are installed on a 20? downward angle for better contact, and the 90? pivoting mounting plate makes installation fast and accurate.
Bar hangers can fit onto T-Bar spline with additional slots and holes for special mounting methods if necessary.
ETL listed for through-branch circuit wiring and has four ½" KOs, one ¾" KO and four Romex knockouts with true pry-out slots and strain clamps.
Integral fluorescent ballast.
Thermally Protected Compact Fluorescent Non-IC housing.
Adjustable Socket bracket.
Wire through junction box.
Preinstalled adjustable bar hangers.
Dependable, favorable design and effortless installation.
7-¼" height allows use in 2"x 8" joist construction.
Special screw on the frame locks bar hangers in place which prevents the housing from any movement once installed.
Gasket to prevent air flow from heated or air conditioned spaces.
Meets all national air flow requirements.
ETL and C-ETL listed
For Damp location
For Feed-through wiring